Video from YouTube (Tavrida Electric – Russia circuit breaker operating mechanism)
- Closing operation: Electrical closing command starts the discharge of pre-charged capacitor bank of control module into the actuator coil When the contact gap is over, the movable contact of VI stops,
the armature gap’’ compressing the contact pressure spring and opening spring that store the energy for
the future opening operation At the end of the compression gap the armature latches magnetically to the yoke. in the closing of the magnetic system the coil current further increases to produce a magnetic field to saturate the magnets and provide the power of the permanent magnets enough to hold the armature in the closed position after the coil current has been cut off by a control module.
- Opening operation: To open the breaker the current of opposite polarity, derived from the opening capacitor in the control module, passes through the coil for few milliseconds. This current partially demagnetizes the magnets and reduces the magnetic holding force in the armature. When the force of charged opening and contact pressure springs exceeds the magnetic force, the armature releases from the yoke, rapidly tear off the contact of VI This film show Tavrida company magnetics actuator operating mechanism.
Hello, I happened to see some knowledge about magnetic circuit breaker on the website. Thank you very much for sharing. Now I have some doubts to discuss with you. Would you please leave a contact information?
Please connect me on LinkedIn.
More information about me:
My LinkedIn profile :